Buy ASTM D R GUIDE FOR FLOOD TESTING HORIZONTAL WATERPROOFING INSTALLATIONS from SAI Global. note that ASTM D “Flood Testing Horizontal Waterproofing Installations” is the ASTM method from which this. Technical Data Sheet draws. ASTM D() – Standard Guide for Flood Testing Horizontal Waterproofing Installations0 item(s) – $ View Basket Welcom.
|Published (Last):||28 September 2010|
|PDF File Size:||8.50 Mb|
|ePub File Size:||18.29 Mb|
|Price:||Free* [*Free Regsitration Required]|
Work Item s – proposed revisions of this standard. See also ACI Note 2 — Increasing the amount of water forming a hydrostatic head beyond sstm 4 in.
Certification Formally confirming that your products and services meet all trusted external and internal standards. The effects shall be analyzed by a licensed structural engineer prior to placement of additional loads. Flood testing is considered to be completed if no leaks are identified to have occurred during the test period and the membrane and flashings are awtm.
If a protection layer is required for flood tested, the f5957 practice is that a temporary protection layer be loose laid and removed prior to testing of the waterproofing system. Need help or have a question?
Water height is maintained so as not to exceed a minimum level of 2 inches below the edge of flashings.
Following the completion of the repairs and curing of materials, the area is retested under the same conditions as the initial flood test. Auditing Consulting Sourcing Training.
Standard Guide for Flood Testing Horizontal Waterproofing Installations
D Terminology Relating to Roofing and Waterproofing. Waterproofing membrane and flashings should zstm inspected and deficiencies repaired. Inspection Validating the specifications, value and safety of your raw materials, products and assets. Applicable waterproofing membrane installations that may be tested using this guide are fully adhered or bonded sheet membranes, liquid or fluid applied d59557, or loose laid sheet membranes.
Formally confirming that your products and services meet all trusted external and internal standards. The values given in parentheses are for information only. The effects of equipment, planters, or other movable objects present within the test area should be considered.
Assurance Enabling you to identify and mitigate the intrinsic risk in your operations, supply chains and business processes. Test area is flooded with water asfm achieve a minimum cover of 1 inch but not exceed a maximum depth of 4 inches at the lowest point.
Historical Version s – view previous versions of standard. Lateral loads will be imposed on curbs or walls used for containment aetm the water during the test procedures and their effect should be accounted for. If leakage is detected during the test period, water is immediately drained from the test area.
ASTM D – 98 Standard Guide for Flood Testing Horizontal Waterproofing Installations
Applies for fully adhered or bonded sheet membranes, liquid or fluid applied membranes or loose laid sheet membranes of waterproofing installed on parking garages and plaza deck types over habitable spaces or on elevated structures. Overflows are provided in the containment assemblies, when needed, at 5 inches above low point on the test surface so as not to exceed the structural capacity of the substrate. Testing should occur prior to the installation of drainage layer, protection layer, pavers or overburden.
Ponded water zstm freeze and become adhered to the waterproofing system d597 in pulling or tearing of the flashings away from the substrate or may break interior corners. Global Reach Intertek is the industry leader with over 42, people in 1, locations in over countries. Critical locations shall be monitored during the duration of the test period. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
Validating the specifications, value and safety of your raw materials, products and assets. This standard astn not intended for use on building roofing systems.
Link to Active This link will always route to the current Active version of the standard. Testing is performed for a minimum of 24 hours and zstm of 72 hours when rainfall is not forecasted to occur. If the product does not meet the performance criteria, additional remediation may be required to pass. Containment assemblies are composed of a sacrificial sheet or a polyethylene sheet adhered to the surface of the waterproofing membrane using a watertight seal duct tape.
Testing Evaluating how your products and services meet and exceed quality, safety, sustainability and performance standards.
ASTM D – 98() Standard Guide for Flood Testing Horizontal Waterproofing Installations
Evaluating how your products and services meet and exceed quality, safety, sustainability and performance standards. Ast containment assembly is constructed to be nondestructive, non-penetrating of the waterproofing installation and easily removable. Whether your business is local or global, we can ensure your products meet quality, health, environmental, safety, and social accountability standards for virtually any market around the world.
Enabling you to identify and mitigate the intrinsic risk in your operations, supply chains and business processes. Assurance Testing Inspection Certification. Through our network of over 43, people in 1, laboratories and offices in countries, Intertek provides quality and safety solutions to a wide range of industries around the world.